This a single family home or multi-unit building? Do you know brand /make of shower valve and/or lav faucet?Do you have hot water recirculating system and if so can you post a picture of it and your 2 fixtures that are giving you trouble Turn the one of the stop valves to lav off 100%. See if the shower returns to normal. Next try this: Do you have any 2 handle faucets anywhere in the house?Turn off the cold supply to the water heater. Open the hot only on a 2 handle faucet. You should get no water out of that faucet once the pressure has drained down. A continuous flow would mean you have a cross over somewhere. Could be the shower valve. go listen to all the single handle fixtures (in closed position) and see if you can hear water passing through them. No 2 handle faucets? Then close the cold stop to a mixing faucet. when you open that faucet you should get no water flow because hot is off at heater. I'll tell you the same I tell customers, If your valves don't work, I can't properly diagnose your problem.
Integrating an additional bathroom into the home can bring property owners two significant benefits
As Calgarians know, snowstorms in September aren?t unheard of. And while the last couple of years h
James Blue of Fayetteville, N.C. is driving happier this holiday season ? in his new 2015 Jeep Wran
There?s more to crafting a bathroom for children than just adding kids bathroom decor to a room. Ex
When dealing with a stopped-up toiler or a clogged drain, one often encounters a certain philosophi
Most homes in Anaheim, Irvine, Fullerton, Garden Grove, and throughout Orange County, CA were built